Typical Progeamming Procedure
Calculate the gallon capacity of the system, subtract the necessary reserve requirement and set the gallons required by lifting the gallon dial and rotating it so that the number of gallon required is aligned with the white dot on program wheel gear. Release and check for firm engagement with gear.
Note: To set meter capacity at initial start-up, either:
1. Rotate manual regeneration knob one full revolution.
2. Rotate program wheel manually clockwise and align white dot with capacity arrow.
This precedure must be followed any time the program wheel setting is changed.
Set Time of Day:
Press and hold the red button in to disengage the 24 hour gear.
Turn the 24 hour gear until the actual time of day is at the time of day pointer.
Release the red button to again engage the 24 hour gear.
How to Manually Regenerate Your Water Condition At Any time:
Turn the manual regeneration knob clockwise one “click”.
This dlight movement of the manual regeneration knob engages the program wheel and starts the regeneration program.
The black center knob will make one revolution in the following approximately three hours and stop in the position shown in the drawing.
In any event, conditioned water may be drawn after rinse water stops flowing from the water conditioner drain line.
Immediate Regeneration Timers:
These timers do not have a 24 hour gear. Setting the gallons on the program wheel and manual regeneration procedure are the same as previous instructions.